Where did all our water go? Minimize lost water
Why don’t all of our individual water service meters add up to the master meter? Municipalities ask this question all the time. The goal is to account for all the water. Our clients want to know if water is being lost through a distribution system leak or if there is an error in how water use is measured. Even more importantly, they want to know how to better tally water use going forward and develop systems to minimize water loss.
Here’s our approach to get to the bottom of unaccounted-for-water…
Determine amount of water loss
Perform an audit of the last five years of water production versus consumption. The study investigates losses through normal water system maintenance, fire department use, construction usage and the identification of non-metered users.
Review of the water meter program
Investigate the following parts of you water program for issues:
- Age of water meters
- Volume of measurements during the meter life as accuracy drops over the registration of large volumes of water
- Frequency of large meter testing
- Application and change-out schedules for water meters
- Water meter reading system
Make sure the rate multipliers match the meters. For example, a 5/8-inch water meter may have one fixed zero, while a one-inch meter may have two or three fixed zeros. It’s important the billing office takes this into account, especially when a community has compound water meters that have both a high and low register.
Detect water distribution system leaks
Use leak detection equipment to survey the entire water distribution system; sounding for leaks in fire hydrants, curb stops, corporation stops and watermain valves. This identifies leaks in the watermains and/or water service connections. Each location with a leak is identified on a water distribution system map and onsite with marking paint. Paint colors – coded by the local utility – mark the leaks on graded system as urgent, moderate or minor. This helps the community plan future capital improvements.
Filter by Expertise
LID retrofit fulfills unique benefits: walking trail, native plantings, sustainable facility
January 31, 2018
Cost estimate versus proposal, the difference matters
January 23, 2018
Military engineers address challenge of resilience
January 3, 2018
about 11 hours ago
Springfield-Branson National Airport rescue facility completed on fast-tracked schedule https://t.co/LNAD1uxYj1… https://t.co/L0N02UEEdh
about 13 hours ago
Raj Sheth is the @IBMadison Lifetime Achievement award winner in large measure because of Mead & Hunt’s status as… https://t.co/BjW0dK3bkH